category：Machinery and industry equipment / date：2023-03-04 15:14:29 / browse：136 / comment：3
Common problems of tap changer of power transformerDuring no-load test run, the transformer shall be connected with the working voltage from the switching power supply side, and then make the working voltage impulse closing.LovichPower saving analysis of transformers has always been based on whether the utilization rate of transformer capacity is less than a certain standard value. Whether transformers are environmental protection and energy saving specifications. In fact, sometimes such specifications are not saving electromagnetic energy, resulting in four wiring groups: & ldquo; y, Y & rdquo;, & ldquo; D, & ldquo; y, D & rdquo; and & ldquo; D, D & rdquo;. In China, only & ldquo; y, Y & rdquo; and & ldquo; y, it will not be upgraded. All marks show that with neutral line, it will not be upgraded The letter N after the English letter Y indicates that the neutral line has transformer grounding wire. Yn wiring group, when UAB and UAB overlap, the minute hand points to . & ldquo; & rdquo; in the new wiring group, it is indicated by & ldquo; & rdquo.Al Baqalitah,The capacity and working voltage are different. The dry-type transformer is generally suitable for distribution equipment. The capacity is generally below kVA and the working voltage is below KV, which also ensures the rated voltage of kV; Oil immersed transformers are generally suitable for distribution equipment.How to reduce the failure of dry-type transformer?After tightening the loose bolts, and solve the bolts that are likely to leak, so as to achieve the goal of complete treatment. Tighten the loose bolts strictly according to the actual operation and processing technology.
Sound in case of phase failureDry type transformer, a static electrical equipment, is used to change the AC current (current) of a certain standard value into another or several types of working voltage (current) with the same frequency and different standard values. According to the supervision sampling inspection data of the third quarter of last year released by AQSIQ, among the kinds of dry-type transformer commodities manufactured by manufacturers in provinces and municipal districts across the country, kinds of commodities were found to be inconsistent with the provisions of relevant specifications, with a compliance rate of %& ldquo; This result mostly shows the quality level of China's dry-type transformer industry at the present stage.(III) dry type transformers of KVA and below can be installed on poles. The distance between its bottom end and the road surface shall not be less than m; The distance between the electrified part and the road surface shall not be less than m.Welcome calls When oil samples are used, the safety and fire safety technical specifications on the spot shall be strictly implemented.The raw materials of Fushi blue can be used for bonding, so that the overall oil leakage of the connector can be greatly controlled; If the actual operation is convenient, the metal shell can also be bonded at the same time to achieve the purpose of leakage treatment.Gradually, high-frequency vibration damping mechanical equipment, such as low-frequency vibration damping platform,LovichPrinciple of power transformer, is installed at the bottom of the dry-type transformer, which can reduce the downward dispersion of the vibration of the dry-type transformer. Then replace the connection between the dry-type transformer and the surrounding engineering buildings, roads, etc. with flexible connection, or use elastic yellow shock absorption mechanical equipment to prevent the vibration from spreading according to the rigid connection. If possible,LovichElectric box transformer, the dry-type transformer room can also be soundproofed and decorated, and sound-absorbing plates and silencing shutters can be used to improve the soundproofing capacity of the dry-type transformer room.
The sampling container is a colorless glass bottle with a wide mouth ground glass plug with a volume of .kg or kg. - bottles shall be collected at a time for analysis and experiment. Labels shall be attached during sampling. Pay attention to the name, source, sampling date, sampling person, weather conditions and other materials of the oil sample.Focus on Development,LovichInsulation grade of oil immersed transformer,The electromagnetic coil is wound with copper power wire or foil and lifted with glass fiber. The epoxy adhesive does not need filling. The vacuum drying equipment is used for degassing and dehumidification. The overall concrete is poured with high fracture toughness resistance to short-circuit faults, common faults and impact. The work is diligent.Once the insulation material of electrical equipment is overheated, the surrounding gas will cause a kind of odor. This kind of odor can be sniffed out by normal patrol staff. When you smell such odor during normal inspection, you should carefully inspect the equipment and parts until you find out the cause.In fact, ground wire is not only a kind of grounding protection. The following describes in detail that ground wire is the general name of grounding system. Ground wire is divided into protective grounding and safety factor grounding device. Among them, safety factor grounding device can be divided into grounding protection, anti electric shock grounding device and anti electromagnetic wave radiation grounding device. Protective grounding is to use it for loop to make the facilities achieve the grounding wire specified by the function.Lovich,For the leakage that has already occurred, find the leakage point first, which can not be ignored. For the position with serious leakage, shovel or sharp punch can be selected. The leakage point can be riveted with special tools for metal materials. After manipulating the leakage, the treatment surface shall be cleaned and tidy. Polymer composite materials are mostly selected for dry consolidation. After dry consolidation, the goal of long-term treatment of leakage can be achieved.On load commissioning:Dry type transformer