category：Machinery and industry equipment / date：2023-02-02 23:40:04 / browse：145 / comment：6
Some are tied with plastic tape, and some immediately press the two edges together, because the socket can not be pressed firmly during installation, and there is still oil leakage without sealing effect.There are many connection groups of dry-type transformers, and the selected structures and connections are also different. Then, what are the groups of dry-type transformers? How to carry out the connection? Or basically introduce it with the network of dry-type transformer manufacturers.Knoke robbery,The dry-type transformer used for power plant voltage transformation is different from the oil transformer. It is strictly prohibited to lead the way at the bottom voltage side to prevent the insulation layer of the dry-type transformer from penetrating due to overvoltage caused by overvoltage at the power grid side or lightning stroke on the line.Sound in case of phase failureMartapuraSound, it will cause great damage.Power transformer factoryUnder normal conditions, the actual operation of the oil immersed transformer shall be undertaken by the on-site operation and maintenance management staff. Within one week of grid connected operation, the operation and maintenance management staff shall improve the safety inspection range of the transformer and immediately communicate and contact with the on-site project staff in case of any problems, so as to ensure the reliable and stable operation of machinery and equipment.
Power transformers are used in all walks of lifeWhen the operating oil is mixed with different types of new oil or used for oil, in addition to the accurate measurement of the cold filter point of the mixed oil, it is also necessary to carry out high and low temperature test and sludge test,Knoke robberyPrice of oil immersed transformer, and observe the sludge accumulation. The accumulation cannot be accessed. The results of the operation of the mixing template are not that the original oil is very poor so it can be managed and used in a mixed manner.Avoid the load operation of power transformer: if the load operation is long-term, short circuit fault between boxes, two-color short circuit fault or short circuit to ground fault and dissolution of oil.Service first,Dry type transformerLoose core screwPlug in the power with full load first, observe and detect that the input and output voltage meets the regulations. At the same time, check whether the equipment has abnormal sound, ignition, odor and other abnormal conditions. If there is any abnormality,Knoke robberyWorking principle of power transformer, please cut off the input switching power supply.
Connection group structure of dry-type transformerWelcome to inquire,The conductor insulation of power transformer is the main part of internal insulation. Some conductors should pass through the middle of electromagnetic coil, or between electromagnetic coil, iron yoke clamp and automobile oil tank wall. Therefore, it is necessary to ensure that this kind of conductor has sufficient insulation compressive strength, i.e. insulation spacing.Maintenance contents of power transformerThe vibration reduction of the grounding device sheet solves the problem of modifying the fixed hard connection between the copper sheet of the grounding device and the dry-type transformer. The original oscillation of the dry-type transformer will be transmitted to the metal in the concrete by the baffle and cause low-frequency noise. Therefore, it must also be changed to produce flexible connection.Knoke robbery,The input and output three-phase power lines shall be connected to phase a, phase B and phase C respectively according to the color of yellow, green and red bus duct of transformer terminal board. The zero line shall be connected to the neutral zero line of transformer voltage, and the grounding wire, transformer casing and its transformer point shall be connected to each other. At ordinary times,Knoke robberyBox transformer 630kVA price, the ground wire and zero wire are led out by the neutral wire of the transformer. (for example, the transformer box shall be matched with the ground wire mark of the shell and connected with each other). Check the input and output lines to ensure they are appropriate and accurate.After no-load test run is normal for h, it can be transferred to on-load operation, and the load shall be gradually increased from %, % and % by grade.The input and output three-phase power lines shall be connected to phase a, phase B and phase C respectively according to the color of yellow, green and red bus duct of transformer terminal board. The zero line shall be connected to the neutral zero line of transformer voltage, and the grounding wire, transformer casing and its transformer point shall be connected to each other. At ordinary times, the ground wire and zero wire are led out by the neutral wire of the transformer. (for example, the transformer box shall be matched with the ground wire mark of the shell and connected with each other). Check the input and output lines to ensure they are appropriate and accurate.