category：Machinery and industry equipment / date：2023-03-10 16:45:34 / browse：112 / comment：6
When the new oil filled by the power transformer and the oil sample that has just been considered are used, the oil sample can be used only after sufficient standing.After sampling, bind the laminated glass stopper firmly with clean paper or cloth to prevent dirt and water from contaminating the bottle stopper.Aitos, common faults of iron core will occur. Don't worry. Contact the transformer manufacturer,AitosTechnical parameters of scb10 dry type transformer, and the manufacturer will assign professional technicians for inspection. The main reasons are as follows:The whole process of hanging the core of dry-type transformer is more critical, and there are many situations that the hanging core of dry-type transformer must pay special attention to. Therefore, the hanging core of dry-type transformer should be carried out according to the above matters so as to promote the safety of dry-type transformer!Songbor,Fault judgment of power transformerPerformance and main parameters of common metal composites, preparation treatment of thick steel plate, blanking process, production and manufacturing process and quality standards of automobile oil tank, riser, coupling and oil storage tank cabinet, welding leakage test and NDT technology, surface treatment process and quality standards, copper, Production process and quality standard of aluminum shield; Body suit iron insertion process, wire installation process, body dryness solution and dry transformer oil solution process, vacuum pump oil immersion, general installation process, leakage test and leakage detection process and quality standards. Performance parameters of key work clothes, machinery and equipment of each process flow; The natural working environment is basically regulated.Dry type transformer factory
Before no-load impulse closing,AitosHow much is a 500 KVA box transformer, the transformer shall be placed for h, and the rising seat and waterproof sleeve installed with vent plug shall be deflated on time.Step up process of dry-type transformer?Deterioration damage of transformer core insulationApplication process,The manufacturing process of dry-type transformer is very process, and must be technically as a certain pillar. Only in that way the performance of dry-type transformer will be more stable. What are the common manufacturing processes and steps of dry-type transformer?Noise pollution control and prevention measures of dry-type transformerPower transformer plant
Avoid inadvertent damage of insulation during maintenance: when repairing the hanging core of power transformer, special attention shall be paid to the maintenance of solenoid coil or insulating waterproof sleeve. If there is scratch damage, it shall be handled properly.offer,The tail end of the high-voltage winding head and the middle tap are made of copper inserts and embedded parts with good strength and stiffness, which is conducive to adjusting the data and has a unique and neat style.The equipment can eliminate the shortcomings found in the patrol inspection, clean the porcelain waterproof casing casing, remove and replace the cracked or brittle leather pad, check and tighten the node, replenish the oil with less oil,Aitos630 dry type power transformer, check and replace the silica gel of the breathing mask, etc.Dry type transformer oscillation is solved by applying vibration damping platform to dry-type transformer and carrying out low-frequency vibration reduction management, which can control the oscillation below .%, and then reduce the building structure noise transmitted by dry-type transformer oscillation.Aitos,It will also produce many faults, effectively deal with various faults of oil immersed transformer, make full use of the performance indicators and advantages of oil immersed transformer, and short-circuit fault is more general.High voltage fuse of transformer breaks one phase;The representative mode of connection group of dry-type transformer is: English capital letters indicate the wiring on the primary side (or primary side), and English letters indicate the wiring on the secondary side (or secondary side). Y (or y) is star wiring, and D (or D) is triangular wiring.